БИЛЕТ № 1

1

Что называется электроустановкой?

Совокупность машин, аппаратов, линий и вспомогательного оборудования (вместе с сооружениями и помещениями, в которых они установлены), предназначенных для производства, преобразования, трансформации, передачи, распределения электрической энергии и преобразования ее в другой вид энергии.

2

Каким требованиям должны удовлетворять работники, принимаемые для выполнения работ в электроустановках?

Работники, принимаемые для выполнения работ в ЭУ, должны иметь профессиональную подготовку, соответствующую характеру работы. При отсутствии профессиональной подготовки такие работники должны быть обучены (до допуска к самостоятельной работе) в специализированных центрах подготовки персонала.

3

Кому предоставлено право выдачи распоряжений для проведения работ в электроустановках напряжением до 1000 В?

Право выдачи распоряжений предоставляется работникам из числа административно-технического персонала организации, имеющим группу IV – в электроустановках напряжением до 1000 В

4

Какое значение напряжения индикации должно быть для указателей напряжения до 1000 В?

Не более 50 В.

5

Какие действия необходимо предпринять для оказания помощи пострадавшему, который находится в состоянии комы (нет сознания, но есть пульс)?

Положить пострадавшего на живот, удалить слизь и содержимое желудка из ротовой полости, приложить холод к голове.

6

Где должны размещаться первичные средства пожаротушения?

Размещение первичных средств пожаротушения в коридорах, проходах не должно препятствовать безопасной эвакуации людей. Их следует располагать на видных местах вблизи от выходов из помещений на высоте не более 1,5 м.

БИЛЕТ № 2

1

Что должно быть использовано для защиты от поражения электрическим током в случае повреждения изоляции при косвенном прикосновении?

Для защиты при косвенном прикосновении должны быть приняты следующие меры:

- защитное заземление;

- автоматическое отключение питания;

- уравнивание потенциалов;

- выравнивание потенциалов;

- двойная или усиленная изоляция;

- сверхнизкое (малое) напряжение;

- защитное электрическое разделение цепей;

- изолирующие (непроводящие) помещения, зоны, площадки.

2

За что несут персональную ответственность работники, проводящие ремонт оборудования?

За нарушения в работе, вызванные низким качеством ремонта.

3

Разрешается ли включать в бригаду работников с группой II для работы в электроустановках.

В состав бригады на каждого работника, имеющего группу III, допускается включать одного работника, имеющего группу II, но общее число членов бригады, имеющих группу II, не должно превышать трех.

4

Какие требования предъявляются к страховочному (удерживающему) канату?

До перепада высот всегда должно оставаться расстояние, примерно равное длине одного шага человека 0, 5 м.

Для страховки применяются стальные, хлопчатобумажные канаты или канаты из капронового фала. Стальные канаты должны соответствовать государственному стандарту. Хлопчатобумажный канат должен быть диаметром не менее 15 мм, канат из капронового фала – не менее 10 мм.

Срок годности средств защиты из синтетических материалов при соблюдении правил эксплуатации и хранения определяется в документации изготовителя, но не должен превышать 2 года или 400 часов эксплуатации.

5

Какой порядок действий оказания первой помощи пострадавшему установлен в случае обморока?

Убедиться в наличии пульса на сонной артерии;

освободить грудную клетку от одежды и расстегнуть поясной ремень;

приподнять ноги; надавить на болевую точку.

6

Какие должны быть действия сотрудника организации, обнаружившего пожар или признаки горения?

Каждый гражданин при обнаружении пожара или признаков горения (задымление, запах гари, повышение температуры и т.п.) должен:

- незамедлительно сообщить об этом по телефону в пожарную охрану (при этом необходимо назвать адрес объекта, место возникновения пожара, а также сообщить свою фамилию):

- принять по возможности меры по эвакуации людей, тушению пожара и сохранности материальных ценностей.

БИЛЕТ № 3

1

Какая классификация помещений в отношении опасности поражения людей электрическим током установлена нормативными документами?

В отношении опасности поражения человека электрическим током различаются

1.Помещения без повышенной опасности, в которых отсутствуют условия, создающие повышенную или особую опасность;

2. Помещения с повышенной опасностью, характеризуются наличием в них одного из условий:

а) сырости 75%;

б) токопроводящей пыли; токопроводящих полов;

г) высокой температуры 35%;

д) возможности одновременного прикосновения человека к имеющим соединение с землей технологическим аппаратам, механизмам и т.п., с одной стороны, и к металлическим корпусам электрооборудования с другой;

3.Особо опасные помещения, характеризуются наличием в них следующих условий, создающих особую опасность:

а) особой сырости 100%;

б) химически активной или органической средой;

в) одновременно двух или более условий повышенной опасности;

Территории размещения наружных электроустановок приравниваются к особо опасным помещениям.

2

Какое напряжение для питания переносных электрических светильников должно применяться в помещениях с повышенной опасностью?

Для питания переносных (ручных) электрических светильников в помещениях с повышенной опасностью и в особо опасных помещениях должно применяться напряжение не выше 50 В.

3

Разрешается ли применение землеройных машин, отбойных молотков, ломов и кирок для рыхления грунта над кабелем, связанного с его раскопкой?

Применение землеройных машин, отбойных молотков, ломов и кирок для рыхления грунта над кабелем разрешается производить на глубину, при которой до кабеля остается слой грунта не менее 30 см. Остальной слой грунта должен удаляться вручную лопатами.

4

Какое минимальное сечение (кв.мм) проводов переносных заземлений установлено в электроустановках напряжением до 1000 В?

Сечение не менее 16 мм².

5

Какая последовательность действий принята для оказания первой помощи на месте происшествия?

1. Если нет сознания и нет пульса на сонной артерии – приступить к реанимации.

2. Если нет сознания, но есть пульс на сонной артерии – повернуть на живот и очистить ротовую полость.

3. При артериальном кровотечении – наложить жгут.

4. При наличии ран – наложить повязки.

5. Если есть признаки переломов костей конечностей – наложить транспортные шины.

6

Что должно быть выполнено на каждом объекте (организации) для обеспечения пожарной безопасности?

На каждом предприятии должны быть разработаны инструкции о мерах пожарной безопасности

БИЛЕТ № 4

1

При каком минимальном значении напряжения переменного и постоянного тока следует выполнять защиту от косвенного прикосновения в помещениях без повышенной опасности?

Защиту при косвенном прикосновении следует выполнять во всех случаях, если напряжение в электроустановке превышает 50 В переменного тока и 120 В постоянного тока.

2

На какой состав подразделяется электротехнический персонал?

Электротехнический персонал предприятий подразделяется:

- административно-технический персонал;

- оперативный;

- ремонтный;

- оперативно - ремонтный персонал.

3

В каком виде разрешено оформлять наряд-допуск на организацию работ в электроустановках?

Наряд оформляется в двух экземплярах. При передаче по телефону, радио наряд выписывается в трех экземплярах. В последнем случае работник, выдающий наряд оформляет один экземпляр, а работник, принимающий текст в виде телефонограммы или радиограммы, факса или электронного письма, заполняет два экземпляра наряда и после проверки указывает на месте подписи выдающего наряд его фамилию и инициалы, подтверждая правильность записи своей подписью. Наряд также разрешено оформлять в электронном виде и передавать по электронной почте.

4

Какие изолирующие электрозащитные средства в электроустановках напряжением до 1000 В относятся к основным?

К основным электрозащитным средствам в электроустановках напряжением до 1000 В относятся:

- изолирующие штанги всех видов;

- изолирующие клещи;

- указатели напряжения;

- электроизмерительные клещи;

- диэлектрические перчатки;

- ручной изолирующий инструмент.

5

Какие установлены правила реанимации, независимо от количества участников оказывающих помощь.

2 «вдоха» искусственного дыхания делают после 30 надавливаний на грудину.

6

Огнетушители, их типы, правила применения и пользования.

Пенные огнетушители применяют для тушения пеной начинающихся загораний почти всех твердых веществ, а также горючих и легковоспламеняющихся жидкостей на площади не более 1м2

Углекислотные огнетушители предназначены для тушения загораний на электрифицированном транспорте, а так же электроустановок под напряжением до 380 В.

Порошковые огнетушители

Используют для тушения небольших очагов загораний горючих жидкостей, газов, ЭУ напряжением до 1000В.

БИЛЕТ № 5

1

Какие из условий относят помещения к особо опасным помещениям в отношении опасности поражения людей током

Особо опасные помещения, характеризуются наличием в них следующих условий, создающих особую опасность:

а) особой сырости; химически активной или органической средой;

в) одновременно двух или более условий повышенной опасности (влажность 75%, температура 35%, корпуса)

Территории размещения наружных электроустановок приравниваются к особо опасным помещениям

2

Какие надписи должны быть нанесены на штепсельных розетках в помещениях с использованием напряжения двух и более номиналов?

В помещениях, в которых используется напряжение двух или более номиналов, на всех штепсельных розетках должны быть надписи с указанием номинального напряжения.

3

Какие работы относятся к работам на высоте?

К работам на высоте относятся работы, когда:

а) существуют риски, связанные с возможным падением работника с высоты 1,8 м и более;

б) работник осуществляет подъем или спуск, превышающий по высоте 5 м, по вертикальной лестнице, угол наклона которой к горизонтальной поверхности более 75°;

в) работы производятся на площадках на расстоянии ближе 2 м от не огражденных перепадов по высоте более 1, 8 м, а так же если высота ограждения этих площадок менее 1,1 м;

4

На какие виды подразделяются плакаты и знаки безопасности?

Плакаты и знаки безопасности предназначены:

запрещающие – для запрещения действия с коммутационными аппаратами, при ошибочном включении которых может быть подано напряжение на место работы (Не включать! Работают люди.);

предупреждающие – для предупреждения об опасности приближения к токоведущим частям, находящимся под напряжением, и передвижения без средств защиты в ОРУ 330 кВ и выше с напряженностью электрического поля выше допустимой (200В, Опасность);

предписывающие – для разрешения конкретных действий только при выполнении определенных требований безопасности (Работать здесь);

указательный – для указания местонахождения различных объектов и устройств (Заземлено).

5

Какие действия выполняются при проведении искусственного дыхания?

Зажать нос, захватить подбородок, запрокинуть голову пострадавшего и сделать максимальный выдох ему в рот (желательно через марлю, салфетку или маску «рот в рот»).

6

Огнетушители, их типы, правила применения и пользования.

Пенные огнетушители применяют для тушения пеной начинающихся загораний почти всех твердых веществ, а также горючих и легковоспламеняющихся жидкостей на площади не более 1м2

Углекислотные огнетушители предназначены для тушения загораний на электрифицированном транспорте, а так же электроустановок под напряжением до 380 В.

Порошковые огнетушители

Используют для тушения небольших очагов загораний горючих жидкостей, газов, ЭУ напряжением до 1000В.

БИЛЕТ № 6

1

Заземление (определение, принцип работы, нормы сопротивления заземления)

Заземление – преднамеренное электрическое соединение какой–либо точки сети, электроустановки или оборудования с заземляющим устройством (землей).

Принцип работы – понижение напряжения между корпусом и землей до безопасного значения, т.е. уменьшение напряжения прикосновения, и следовательно тока протекающего через организм человека.

Нормы – на ОУС=4Ом, нп ТП=8Ом, Тело человека – 1Ком. Сечение проводника до 1000В не менее 16 кв.мм. Свыше 1000В не менее 25 кв.мм.

2

За что несут персональную ответственность работники, непосредственно обслуживающие электроустановки?

За нарушения, происшедшие по их вине, а также за неправильную ликвидацию ими нарушений в работе ЭУ на обслуживаемом участке.

3

Кто имеет право единоличного осмотра электроустановок и электрической части технологического оборудования напряжением до 1000 В?

Единоличный осмотр электроустановок, электротехнической части технологического оборудования имеет право выполнять работник, из числа оперативного персонала, имеющий группу не ниже III, обслуживающий данную электроустановку. Либо работник из числа административно-технического персонала, имеющий группу IV. Право единоличного осмотра предоставляется на основании Организационно распорядительного документов (ОРД) организации (обособленного подразделения).

4

В каком случае можно использовать контрольные лампы для проверки отсутствия напряжения в электроустановках напряжением 0,4 кВ?

Применение контрольных ламп для проверки отсутствия напряжения не допускается.

5

Что необходимо выполнить в случае перелома конечности?

Зафиксировать конечность с помощью складных шин или подручных средств.

При открытых переломах сначала наложить повязку и только затем – шину.

6

К какому классу относятся пожары, связанные с горением электроустановок?

Пожары, связанные с горением электроустановок относятся классу Е.

БИЛЕТ № 7

1

Защитное зануление в электроустановках напряжением до 1 кВ (определение, принцип работы)

Защитное зануление в электроустановках напряжением до 1 кВ – это преднамеренное соединение открытых проводящих частей электроустановки с глухозаземленной нейтралью (нулем).

Принцип работы – превратить пробой на корпус в однофазное короткое замыкание, вызвать срабатывание защиты и отключение электроустановки от питающей сети в минимально короткий срок.

2

Какое напряжение для питания переносных электрических светильников должно применяться в наружных установках?

При работах в особо неблагоприятных условиях и в наружных установках - не выше 12 В.

3

Охрана труда при организации работ в электроустановках, выполняемых по перечню работ в порядке текущей эксплуатации.

Небольшие по объему ремонтные работы и работы по техническому обслуживанию, выполняемые в течение рабочей смены и включенные в перечень работ. Выполняются оперативным или оперативно – ремонтным персоналом на закрепленном за этим персоналом оборудовании (участке). Работа является постоянно разрешенной, не требующей дополнительных распоряжений и проведения целевого инструктажа. Учет работ фиксируется записью в оперативном журнале.

4

Для каких электроустановок предназначены однополюсные указатели напряжения до 1000 В?

Однополюсные указатели, работающие при протекании емкостного тока предназначены для ЭУ только переменного тока.

5

Какие признаки свидетельствуют о внезапной (клинической) смерти пострадавшего?

1. Отсутствие сознания.

2. Нет реакции зрачков на свет.

3. Нет пульса на сонной артерии.

6

Какие электроустановки и электроприборы могут не выключаться по окончании рабочего дня в помещениях без дежурного персонала для обеспечения пожарной безопасности?

Дежурное освещение, установки пожаротушения и противопожарного водоснабжения, пожарной и охранно-пожарной сигнализации. Другие электроустановки и электротехнические изделия ( в т.ч. в жилых помещениях) могут оставаться под напряжением, если это обусловлено их функциональным назначением и (или) предусмотрено требованиями инструкции по эксплуатации.

БИЛЕТ № 8

1

Какое цветовое обозначение установлено для шины, используемой в качестве нулевой защитной в ЭУ напряжением до 1000 В с глухозаземленной нейтралью?

Нулевые защитные проводники в электроустановках напряжением до 1 кВ с глухозаземленной нейтралью, в т.ч. шины, должны иметь буквенное обозначение РЕ и цветовое обозначение чередующимися продольными или поперечными полосами одинаковой ширины (для шин от 15 до 100 мм) желтого и зеленого цветов.

2

Какие виды проверок знаний установлены для электротехнического персонала?

Проверка знаний работников подразделяется на первичную и периодическую (очередную и внеочередную).

3

Какие работы в электроустановках относятся к специальным, право на проведение которых отражается в удостоверении после проверки знаний работника?

К специальным работам относится:

- работы, выполняемые на высоте более 5 м от поверхности земли, перекрытия или рабочего настила,

- верхолазные работы;

- работы под напряжением на токоведущих частях;

- испытания оборудования повышенным напряжением (за исключением работ с мегаомметром);

- работы под наведенным напряжением

4

Каким образом следует проверять перчатки диэлектрические на отсутствие прокола?

Путем скручивания перчаток в сторону пальцев.

5

Какие действия выполняются при проведении искусственного дыхания?

Зажать нос, захватить подбородок, запрокинуть голову пострадавшего и сделать максимальный выдох ему в рот (желательно через марлю, салфетку или маску «рот в рот»).

6

Что должно быть выполнено на каждом объекте (организации) для обеспечения пожарной безопасности?

На каждом предприятии должны быть разработаны инструкции о мерах пожарной безопасности.

БИЛЕТ № 9

1

Какие открытые проводящие части электрооборудования должны быть присоединены к глухозаземленной нейтрали для защиты при косвенном прикосновении?

Требования защиты при косвенном прикосновении распространяются на:

корпуса электрических машин, трансформаторов, аппаратов, светильников и т.п.

2

Какие условия должны быть выполнены перед проведением земляных работ вблизи кабельных трасс?

Раскопки кабельный трасс или земляные работы вблизи них должны производиться только после получения соответствующего разрешения руководства организации, по территории которой проходит КЛ, и организации, эксплуатирующей КЛ. Исполнитель должен обеспечить надзор за сохранностью кабелей на весь период работ, а вскрытые кабели укрепить для защиты от механических повреждений.

3

Разрешается ли при единоличном осмотре электроустановок открывать двери щитов и сборок?

При осмотре электроустановок разрешается открывать двери щитов, сборок, пультов управления и других устройств.

4

В каком случае можно использовать контрольные лампы для проверки отсутствия напряжения в электроустановках напряжением 0,4 кВ?

Применение контрольных ламп для проверки отсутствия напряжения не допускается.

5

В течение, какого времени необходимо проводить реанимацию пострадавшему при внезапной смерти?

При сужении зрачков, но отсутствии сердцебиения реанимацию нужно проводить до прибытия медперсонала.

6

В каком случае работники предприятия должны допускаться к работе в соответствии с правилами пожарной безопасности?

Все работники организаций должны допускаться к работе только после прохождения противопожарного инструктажа

БИЛЕТ № 10

1

Что понимается под косвенным прикосновением?

Электрический контакт людей или животных с открытыми проводящими частями, оказавшимися под напряжением при повреждении изоляции.

2

В каком случае электротехнический персонал обязан пройти стажировку (производственное обучение)?

Электротехнический персонал до назначения на самостоятельную работу или при переходе на другую работу (должность), связанную с эксплуатацией электроустановок, а также при перерыве в работе в качестве электротехнического персонала свыше одного года обязан пройти стажировку (производственное обучение) на рабочем месте.

3

Какой определен порядок установки и снятия переносных заземлений до 1000 В?

Кому разрешено устанавливать и снимать переносные заземления до 1000 В?.

Переносное заземление сначала нужно присоединить к заземляющему устройству, а затем, после проверки отсутствия напряжения, установить на токоведущие части.

Снимать переносное заземление необходимо в обратной последовательности: сначала снять его с токоведущих частей, а затем отсоединить от заземляющего устройства.

Установка и снятие переносных заземлений должны выполняться в диэлектрических перчатках.

Переносные заземления следует присоединять к токоведущим местам, очищенным от краски.

Устанавливать и снимать переносное заземление разрешается одному работнику, имеющему группу III, из числа оперативного или оперативно-ремонтного персонала.

4

Какие плакаты и знаки безопасности относятся к запрещающим?

Плакаты запрещающие:

- НЕ ВКЛЮЧАТЬ! работают люди;

- НЕ ВКЛЮЧАТЬ! работа на линии.

5

При каких показаниях следует немедленно наложить кровоостанавливающий жгут?

1. Алая кровь из раны бьет фонтанирующей струей.

2. Над раной образуется валик из вытекающей крови.

3. Большое кровавое пятно на одежде или лужа крови возле пострадавшего.

6

В каких случаях проводится дозарядка или перезарядка баллонов и емкостей установок пожаротушения?

Баллоны и емкости установок пожаротушения, масса огнетушащего вещества и давление в которых ниже расчетных значений на 10% и более, подлежат дозарядке или перезарядке.

БИЛЕТ № 11

1

Какую функцию выполняют устройства защитного отключения (УЗО), применяемые в ЭУ до 1000 В?

Обеспечение (дополнительной) защиты от прямого прикосновения в электроустановках напряжением до 1000В следует также применять устройства защитного отключения (УЗО) с номинальным отключающим дифференциальным током не более 30 мА.

2

Кому и когда должен сообщить работник, заметивший неисправности электроустановки или средств защиты?

Каждый работник обнаруживший нарушения Правил, а также заметивший неисправности ЭУ или средств защиты, должен немедленно сообщить об этом непосредственному руководителю, а в его отсутствие вышестоящему руководителю.

3

Организационные мероприятия по обеспечению безопасного проведения работ в электроустановках?

Организационными мероприятиями, обеспечивающими безопасность работ в электроустановках, являются:

- оформление наряда, распоряжения или перечня работ, выполняемых в порядке текущей эксплуатации;

- выдача разрешения на подготовку рабочего мести и на допуск к работе;

- надзор во время работы;

- оформление перерыва в работе, перевода на другое место, окончания работы.

4

Какие изолирующие электрозащитные средства в электроустановках напряжением до 1000 В относятся к дополнительным?

К дополнительным электрозащитным средствам для работы в электроустановках напряжением до 1000 В относятся:

- диэлектрические галоши;

- диэлектрические ковры и изолирующие подставки;

- изолирующие колпаки и накладки;

- лестницы приставные, стремянки изолирующие стеклопластиковые.

5

Первая помощь при ушибах, растяжении связок.

К месту ушиба, нужно приложить холод, а затем наложить тугую повязку.

При растяжении связок, помощь заключается в тугом бинтовании, обеспечении покоя поврежденного участка, прикладывании «холода».

6

К какому классу относятся пожары, связанные с горением электроустановок?

Пожары, связанные с горением электроустановок относятся классу Е.

БИЛЕТ № 12

1

Какое расстояние должно быть между доступными одновременному прикосновению проводящими частями в ЭУ до 1000 В, размещенными вне зоны досягаемости?

Расстояние между доступными одновременному прикосновению проводящими частями в ЭУ до 1 кВ должно быть не менее 2,5 м. Внутри зоны досягаемости не должно быть частей, имеющих разные потенциалы. В вертикальном направлении зона досягаемости в электроустановках до 1 кВ должна составлять 2,5 м от поверхности, на которой находятся люди.

2

В каком случае проводится внеочередная проверка знаний?

Внеочередная проверка знаний проводится независимо от срока проведения предыдущей проверки:

- при введении в действие у Потребителя новых или переработанных норм и правил;

- при установке нового оборудования, реконструкции или изменении главных электрических и технологических схем (необходимость внеочередной проверки в этом случае определяет технический руководитель);

- при назначении или переводе на другую работу, если новые обязанности требуют дополнительных знаний;

- при нарушении работниками требований нормативных актов по охране труда;

- по требованию органов государственного надзора;

- по заключению комиссий, расследовавших несчастные случаи;

- при повышении знаний на более высокую группу;

- при проверке знаний после получения неудовлетворительной оценки;

- при перерыве в работе в данной должности более 6 месяцев.

3

Какие работы относятся к работам под наведенным напряжением?

Работы, выполняемые со снятием рабочего напряжения с электроустановки или ее части с прикосновением к токоведущим частям, находящимся под наведенным напряжением более 25 В на рабочем месте или на расстоянии от этих токоведущих частей менее допустимого.

4

К какому виду средств защиты относятся запрещающие плакаты безопасности

Коллективное средство защиты.

5

Какие установлены правила перемещения человека в зоне шагового напряжения?

Передвигаться в зоне «шагового» напряжения следует в диэлектрических ботах или галошах, либо «гусиным шагом» - пятка шагающей ноги, не отрываясь от земли, приставляется к носку другой ноги.

6

Есть ли необходимость устанавливать огнетушители в помещениях, оборудованных автоматическими стационарными установками пожаротушения?

Помещения, оборудованные автоматическими стационарными установками пожаротушения, обеспечиваются огнетушителями на 50% исходя из их расчетного количества.

БИЛЕТ № 13

1

Что следует понимать под прямым прикосновением в электроустановках?

Прямое прикосновение - электрический контакт людей или животных с токоведущими частями, находящимися под напряжением.

2

Продлевается или нет срок действия удостоверения для работников, получивших неудовлетворительную оценку при проверке знаний?

Автоматически продлевается до срока, назначенного комиссией для второй проверки, если нет записанного в журнал проверки знаний специального решения комиссии о временном отстранении работника от работы в электроустановках

3

Допускается ли заменять предохранители в цепях управления, контроля и сигнализации, находящихся под напряжением и под нагрузкой?

Под напряжением и под нагрузкой допускается заменять:

Предохранители во вторичных соединениях или цепях;

Предохранители трансформаторов напряжения;

Предохранители пробочного типа.

4

Какая длина установлена для диэлектрических перчаток?

Длина перчаток должна быть не менее 350 мм.

5

На какое время накладывается жгут при артериальном кровотечении?

Жгут на конечность можно наложить не более чем на 1 час.

6

Что необходимо выполнить при установке на объекте огнетушителей?

Каждый огнетушитель, установленный на объекте, должен иметь порядковый номер, нанесенный на корпус белой краской. На него заводят паспорт по установленной форме.

БИЛЕТ № 14

1

Какие способы обеспечения безопасности обслуживающего персонала установлены в электроустановках

Безопасность обеспечиваться выполнением мер защиты, а также следующих мероприятий:

- соблюдение соответствующих расстояний до токоведущих частей или путем закрытия, ограждения токоведущих частей;

- применение блокировки аппаратов и ограждающих устройств, для предотвращения ошибочных операций и доступа к токоведущим частям;

- применение устройств, для снижения напряженности электрических и магнитных полей до допустимых значений;

- использование средств защиты и приспособлений;

2

С каким персоналом обязательной формой работы (профессиональной подготовки) является дублирование?

С оперативным и оперативно - ремонтным персоналом.

3

Кому должен сообщать работник о замеченных им нарушениях, представляющих опасность для людей, если он не имеет права принять меры по их устранению?

Работник, в случае если он не имеет права принять меры по устранению нарушений требований Правил, представляющих опасность для людей, неисправностей электроустановок, машин, механизмов, приспособлений, инструмента, средств защиты, обязан сообщить об этом своему непосредственному руководителю.

4

Какие плакаты и знаки безопасности относятся к указательным?

Плакат указательный «ЗАЗЕМЛЕНО».

5

Какие признаки определяют наличие у пострадавшего венозного кровотечения

1. Кровь пассивно стекает из раны.

2. Очень темные цвет крови.

6

Пожарная безопасность в производственных помещениях.

Противопожарная безопасность включает в себя комплекс организационных и технических мероприятий.

1) В помещении должна быть инструкция о мерах пожарной безопасности.

2) Необходимо соблюдать чистоту и порядок в помещении.

3) Курить только в специально отведенных местах.

4) Не загромождать проходы в помещении.

5) Осматривать помещение после работы.

Запрещается:

1) Уборка помещений химическими веществами.

2) Применять не калиброванные вставки и жучки.

3) Пользоваться приборами с открытыми спиралями нагрева.

4) Оставлять включенными электроприборы.

5) Хранить легко воспламеняющиеся вещества.

БИЛЕТ № 15

1

Что понимается под электрической сетью с глухозаземленной нейтралью?

Электрическая сеть, в которой нейтраль трансформатора или генератора присоединена непосредственно к заземляющему устройству.

2

Какой вид проверки установлен для работника, повышающего знания на более высокую группу?

Внеочередная проверка знаний.

3

Охрана труда при выполнении технических мероприятий, обеспечивающих безопасность работ со снятием напряжения.

В указанном порядке должны быть выполнены следующие технические мероприятия:

- произведены необходимые отключения и приняты меры, препятствующие подаче напряжения на место работы вследствие ошибочного или самопроизвольного включения коммутационных аппаратов;

- на приводах ручного и на ключах дистанционного управления коммутационных аппаратов должны быть вывешены запрещающие плакаты;

- проверено отсутствие напряжения на токоведущих частях, которые должны быть заземлены для защиты людей от поражения электрическим током;

- установлено заземление;

- вывешены указательные плакаты «ЗАЗЕМЛЕНО», ограждены при необходимости рабочие места и оставшиеся под напряжением токоведущие части, вывешены предупреждающие и предписывающие плакаты.

4

Что обязан выполнять персонал организации перед каждым применением средств защиты?

Перед каждым применением средств защиты персонал обязан проверить его исправность, отсутствие внешних повреждений и загрязнений, а также проверить по штампу срок годности.

5

В каком месте необходимо прижимать артерию в случае артериального кровотечения?

Прижать пальцами или кулаком артерию:

-на конечностях точка прижатия артерии должна быть выше места кровотечения;

-на шее и голове – ниже раны или в ране.

6

Порядок хранения и правила применения пожароопасных веществ и материалов.

В помещения ОУС хранение огнеопасных и легковоспламеняющихся жидкостей и горюче-смазочных материалов - запрещено.

Обтирочные материалы должны храниться в закрытых металлических ящиках емкостью не более 0.5 кубических метра. Пожароопасные вещества должны храниться на складе в специально отведённых местах. Горючие жидкости в железных бочках. Случайно пролитые топливо или масла должны быть немедленно засыпаны песком. В случае воспламенения жидкого топлива или изоляции на токоведущих частях электростанции необходимо пользоваться углекислотным огнетушителем.

БИЛЕТ № 16

1

Каким должно быть сопротивление заземляющего устройства для нейтрали трансформатора при линейном напряжении источника трехфазного тока 380 и 220 В?

Сопротивление заземляющего устройства для нейтрали трансформатора при линейном напряжении источника трехфазного тока:

- 380 В в любое время года должно быть не более 4 Ом;

- 220 В в любое время года должно быть не более 8 Ом.

2

В каком случае проводится очередная проверка знаний?

Очередная проверка знаний должна производиться в следующие сроки:

- для электротехнического персонала, непосредственно организующего и проводящего работы по обслуживанию действующих электроустановок, а также для персонала, имеющего право выдачи нарядов, распоряжений, - 1 раз в год;

- для административно-технического персонала, не относящегося к предыдущей группе, а также для специалистов по охране труда, допущенных к инспектированию электроустановок - 1 раз в 3 года.

3

Когда работники из числа электротехнического персонала должны проходить обучение по оказанию первой помощи пострадавшему?

Работники должны проходить обучение по оказанию первой помощи пострадавшему на производстве до допуска к самостоятельной работе.

4

К какому виду средств защиты относится страховочная привязь

К индивидуальному страховочному снаряжению для работ на высоте

5

При каких показаниях следует переносить пострадавшего только на животе?

1. В состоянии комы.

2. При частой рвоте.

3. В случаях ожогов спины и ягодиц.

4. При подозрении на повреждение спинного мозга, когда в наличии есть только брезентовые носилки.

6

Что необходимо выполнить при установке на объекте огнетушителей?

Каждый огнетушитель, установленный на объекте, должен иметь порядковый номер, нанесенный на корпус белой краской. На него заводят паспорт по установленной форме.

БИЛЕТ № 17

1

В каком случае не требуется выполнять защиту от прямого прикосновения в помещениях без повышенной опасности с электроустановками переменного и постоянного тока?

Защита от прямого прикосновения не требуется, если электрооборудование находится в зоне системы уравнивания потенциалов, а наибольшее рабочее напряжение не превышает 25 В переменного или 60 В постоянного тока в помещениях без повышенной опасности.

2

Какая продолжительность дублирования установлена для оперативного персонала?

Продолжительность дублирования - от 2 до 12 рабочих смен.

3

На какое напряжение должны подключаться переносные электрические светильники:

- в особо опасных помещениях?

- в особо неблагоприятных условиях?

В помещениях с повышенной опасностью и особо опасных переносные электрические светильники должны иметь напряжение не выше 50 В.

При работе в особо неблагоприятных условиях переносные светильники должны иметь напряжение не выше 12 В.

4

Какая периодичность испытаний установлена для диэлектрических резиновых перчаток?

Периодичность испытаний диэлектрических перчаток – 1 раз в 6 месяцев.

5

При каких показаниях следует переносить и перевозить пострадавшего только сидя или полусидя?

1. При проникающих ранениях грудной клетки.

2. При ранениях шеи.

6

Что необходимо выполнить при установке на объекте огнетушителей?

Каждый огнетушитель, установленный на объекте, должен иметь порядковый номер, нанесенный на корпус белой краской. На него заводят паспорт по установленной форме.

БИЛЕТ № 18

1

Защитное зануление в электроустановках напряжением до 1 кВ (определение, принцип работы).

Защитное зануление в электроустановках напряжением до 1 кВ – это преднамеренное соединение открытых проводящих частей электроустановки с глухозаземленной нейтралью (нулем).

Принцип работы – превратить пробой на корпус в однофазное короткое замыкание, вызвать срабатывание защиты и отключение электроустановки от питающей сети в минимально короткий срок.

2

Какая продолжительность дублирования установлена для оперативного персонала?

Продолжительность дублирования - от 2 до 12 рабочих смен.

3

Какие мероприятия необходимо провести с командированным персоналом в организации, где этот персонал будет работать в электроустановках?

Командированный персонал по прибытии на место командировки должен пройти вводный и первичный инструктажи по охране труда. Должен быть ознакомлен с электрической схемой и особенностями электроустановки, в которой им предстоит работать, а работники, которым предоставляется право выдачи наряда, должны пройти инструктаж по схеме электроснабжения электроустановки.

Инструктажи должны быть оформлены записями в журналах инструктажа с подписями командированных работников и работников, проводивших инструктажи.

4

Что обязан выполнять персонал организации перед каждым применением средств защиты?

Перед каждым применением средств защиты персонал обязан проверить его исправность, отсутствие внешних повреждений и загрязнений, а также проверить по штампу срок годности.

5

Какие признаки свидетельствуют о биологической смерти пострадавшего?

1. Высыхание роговицы глаза (появление «селедочного» блеска).

2. Деформация зрачка при осторожном сжатии глазного яблока пальцами.

3. Появление трупных пятен.

6

Огнетушители, их типы, правила применения и пользования.

Огнетушители делятся на переносные (массой до 20 кг) и передвижные (массой не менее 20, но не более 400 кг). По виду применяемого огнетушащего вещества огнетушители подразделяют на:

Пенные огнетушители применяют для тушения пеной начинающихся загораний почти всех твердых веществ, а также горючих и легковоспламеняющихся жидкостей на площади не более 1м2

Углекислотные огнетушители предназначены для тушения загораний на электрифицированном транспорте, а так же электроустановок под напряжением до 380 В.

Порошковые огнетушители

Используют для тушения небольших очагов загораний горючих жидкостей, газов, электроустановок напряжением до 1000В.

БИЛЕТ № 19

1

Что понимается под напряжением прикосновения?

Напряжение между двумя проводящими частями или между проводящей частью и землей при одновременном прикосновении к ним человека.

2

На какой состав подразделяется электротехнический персонал?

Электротехнический персонал предприятий подразделяется:

- административно-технический персонал;

- оперативный;

- ремонтный;

- оперативно - ремонтный персонал.

3

Для каких целей назначается наблюдающий при проведении работ в электроустановках?

Наблюдающий - работник из числа электротехнического персонала, осуществляющий надзор за бригадами, не имеющими права самостоятельного производства работ в электроустановках.

4

Обязательно ли применение диэлектрических перчаток при пользовании однополюсными указателями напряжения до 1000В?

Применение диэлектрических перчаток не допускается.

5

При каких показаниях можно переносить пострадавшего только на спине с приподнятыми или согнутыми в коленях ногами?

1. При проникающих ранениях брюшной полости.

2. При большой кровопотере или при подозрении на внутреннее кровотечение.

6

Какие должны быть действия сотрудника организации, обнаружившего пожар или признаки горения?

Каждый гражданин при обнаружении пожара или признаков горения (задымление, запах гари, повышение температуры и т.п.) должен:

- незамедлительно сообщить об этом по телефону в пожарную охрану (при этом необходимо назвать адрес объекта, место возникновения пожара, а также сообщить свою фамилию):

- принять по возможности меры по эвакуации людей, тушению пожара и сохранности материальных ценностей.

БИЛЕТ № 20

1

Какой цвет установлен для нулевого рабочего проводника электрической сети?

Нулевые рабочие (нейтральные) проводники обозначаются буквой N и голубым цветом.

2

За что несут персональную ответственность работники, непосредственно обслуживающие электроустановки

За нарушения, происшедшие по их вине, а также за неправильную ликвидацию ими нарушений в работе ЭУ на обслуживаемом участке.

3

Кто может назначаться производителем работ, выполняемых по наряду в электроустановках напряжением до 1000 В.

За что отвечает производитель работ?

Производитель работ, выполняемых по наряду в электроустановках напряжением до 1000 В, должен иметь гр. III.

При выполнении работ в подземных сооружениях, где возможно появление вредных газов, должен иметь гр. IV.

Производитель работ отвечает:

- за соответствие подготовленного рабочего места и отдельным указаниям наряда;

- за четкость и полноту целевого инструктажа членов бригады;

- за наличие, исправность и правильное применение необходимых средств защиты, инструмента, инвентаря;

- за сохранность на рабочем месте ограждений, плакатов (знаков безопасности);

- за безопасное проведение работы и соблюдение Правил им самим и членами бригады;

- за осуществление постоянного контроля за членами бригады.

4

Какая периодичность испытаний установлена для ковров резиновых диэлектрических?

В эксплуатации ковры и подставки не испытываются. Их осматривают не реже 1 раза в 6 мес., а также непосредственно перед применением. При обнаружении механических дефектов ковры изымают из эксплуатации и заменяют новыми, а подставки направляют в ремонт.

5

Какие признаки свидетельствуют о биологической смерти пострадавшего?

1. Высыхание роговицы глаза (появление «селедочного» блеска).

2. Деформация зрачка при осторожном сжатии глазного яблока пальцами.

3. Появление трупных пятен.

6

В каком случае работники предприятия должны допускаться к работе в соответствии с правилами пожарной безопасности?

Все работники организаций должны допускаться к работе только после прохождения противопожарного инструктажа.

БИЛЕТ № 21

1

Заземление (определение, принцип работы, нормы сопротивления заземления)

Заземление – преднамеренное электрическое соединение какой–либо точки сети, электроустановки или оборудования с заземляющим устройством (землей).

Принцип работы – понижение напряжения между корпусом и землей до безопасного значения, т.е. уменьшение напряжения прикосновения, и следовательно тока протекающего через организм человека.

Нормы – на ОУС=4Ом, нп ТП=8Ом, Тело человека – 1Ком. Сечение проводника до 1000В не менее 16 кв.мм. Свыше 25 кв.мм

2

В каком случае проводится внеочередная проверка знаний?

Внеочередная проверка знаний проводится независимо от срока проведения предыдущей проверки:

- при введении в действие у Потребителя новых или переработанных норм и правил;

- при установке нового оборудования, реконструкции или изменении главных электрических и технологических схем (необходимость внеочередной проверки в этом случае определяет технический руководитель);

- при назначении или переводе на другую работу, если новые обязанности требуют дополнительных знаний;

- при нарушении работниками требований нормативных актов по охране труда;

- по требованию органов государственного надзора;

- по заключению комиссий, расследовавших несчастные случаи;

- при повышении знаний на более высокую группу;

- при проверке знаний после получения неудовлетворительной оценки;

- при перерыве в работе в данной должности более 6 месяцев.

3

Кто может назначаться допускающим в электроустановках напряжением до 1000 В.

За что отвечает допускающий?

Допускающие должны назначаться из числа оперативного персонала и иметь группу III в электроустановках до 1000 В.

Отвечает за правильность и достаточность принятых им мер безопасности по подготовке рабочих мест и соответствие их мероприятиям, указанным в наряде или распоряжении, характеру и месту работы, за правильный допуск к работе, а также за полноту и качество проводимого им целевого инструктажа.

4

Какие изолирующие электрозащитные средства в электроустановках напряжением до 1000 В относятся к основным?

К основным электрозащитным средствам в электроустановках напряжением до 1000 В относятся:

- изолирующие штанги всех видов;

- изолирующие клещи;

- указатели напряжения;

- электроизмерительные клещи;

- диэлектрические перчатки;

- ручной изолирующий инструмент.

5

Какие признаки определяют наличие обморока у человека?

1. Кратковременная потеря сознания (не более 3-4 минут).

2. Потери сознания предшествуют: резкая слабость, головокружение, звон в ушах и потемнение в глазах.

6

Есть ли необходимость устанавливать огнетушители в помещениях, оборудованных автоматическими стационарными установками пожаротушения

Помещения, оборудованные автоматическими стационарными установками пожаротушения, обеспечиваются огнетушителями на 50% исходя из их расчетного количества.

БИЛЕТ № 22

1

Какое цветовое обозначение установлено для шин ЭУ переменного трехфазного тока?

При переменном трехфазном токе: шины фазы А - желтым, фазы В - зеленым, фазы С – красным цветом.

2

Какое напряжение для питания переносных электрических светильников должно применяться в помещениях с повышенной опасностью?

Для питания переносных (ручных) электрических светильников в помещениях с повышенной опасностью и в особо опасных помещениях должно применяться напряжение не выше 50 В.

3

Где вывешиваются запрещающие плакаты при выполнении технических мероприятий, обеспечивающих безопасность работ со снятием напряжения на присоединениях напряжением до 1000 В, не имеющих коммутационных аппаратов?

На присоединениях напряжением до 1000 В, не имеющих коммутационных аппаратов, запрещающий плакат «Не включать! Работают люди» должен быть вывешен у снятых предохранителей.

4

На какие виды подразделяются плакаты и знаки безопасности?

Плакаты и знаки безопасности предназначены:

запрещающие – для запрещения действия с коммутационными аппаратами, при ошибочном включении которых может быть подано напряжение на место работы (Не включать! Работают люди.);

предупреждающие – для предупреждения об опасности приближения к токоведущим частям, находящимся под напряжением, и передвижения без средств защиты в ОРУ 330 кВ и выше с напряженностью электрического поля выше допустимой (200В, Опасность);

предписывающие – для разрешения конкретных действий только при выполнении определенных требований безопасности (Работать здесь);

указательный – для указания местонахождения различных объектов и устройств (Заземлено).

5

Какой установлен порядок действий в случае отравления пострадавшего ядовитыми газами?

Вынести на свежий воздух.

В случае отсутствия сознания и пульса на сонной артерии – приступить к комплексу реанимации.

В случаях потери сознания более 4 минут – повернуть на живот и приложить холод к голове.

Вызвать «скорую помощь».

6

Где должны размещаться первичные средства пожаротушения?

Размещение первичных средств пожаротушения в коридорах, проходах не должно препятствовать безопасной эвакуации людей. Их следует располагать на видных местах вблизи от выходов из помещений на высоте не более 1,5 м.

БИЛЕТ № 23

1

Какой цвет установлен для совмещенных нулевых защитных и нулевых рабочих (PEN) проводников?

Совмещенные нулевые защитные и нулевые рабочие проводники должны иметь буквенное обозначение РЕN и цветовое обозначение: голубой цвет по всей длине и желто-зеленые полосы на концах.

2

За что несут персональную ответственность работники, проводящие ремонт оборудования?

За нарушения в работе, вызванные низким качеством ремонта.

3

Что необходимо предварительно выполнить до начала работы в кабельных подземных сооружениях?

Кто может выполнять работы в подземных кабельных сооружениях?

До начала и во время работы в подземных сооружениях необходимо:

- обеспечить естественную или принудительную вентиляцию

- обеспечить связь между работником, выполняющим работу и страхующими

- взять анализ на содержание в воздухе кислорода (не менее 20%)

Работы в подземных кабельных сооружениях, а также их осмотр со спуском в них должны выполняться по наряду не менее чем тремя работниками, двое из которых – страхующие. Производитель работ должен иметь группу IV

4

Какие изолирующие электрозащитные средства в электроустановках напряжением до 1000 В относятся к дополнительным?

К дополнительным электрозащитным средствам до 1000 В относятся:

- диэлектрические галоши;

- диэлектрические ковры и изолирующие подставки;

- изолирующие колпаки и накладки;

- лестницы приставные, стремянки изолирующие стеклопластиковые.

5

Как обрабатывать ожоги на месте происшествий?

Без нарушения целостности ожоговых пузырей – подставить под струю холодной воды на 10-15 минут и/или приложить холод на 20-30 минут.

С нарушением целостности ожоговых пузырей и кожи – накрыть сухой чистой тканью, поверх приложить холод.

6

Какие должны быть действия сотрудника организации, обнаружившего пожар или признаки горения?

Каждый гражданин при обнаружении пожара или признаков горения (задымление, запах гари, повышение температуры и т.п.) должен:

- незамедлительно сообщить об этом по телефону в пожарную охрану (при этом необходимо назвать адрес объекта, место возникновения пожара, а также сообщить свою фамилию):

- принять по возможности меры по эвакуации людей, тушению пожара и сохранности материальных ценностей.

БИЛЕТ № 24

1

Что должно быть использовано для защиты от поражения электрическим током в нормальном режиме при прямом прикосновении?

Для защиты от поражения электрическим током в нормальном режиме должны быть применены по отдельности или в сочетании следующие меры защиты от прямого прикосновения:

- основная изоляция токоведущих частей;

- ограждения и оболочки;

- установка барьеров;

- размещение вне зоны досягаемости;

- применение сверхнизкого (малого) напряжения - не превышающее 50 В переменного и 120 В постоянного тока.

Для доп. защиты от прямого прикосновения в электроустановках напряжением до 1 кВ следует также применять устройства защитного отключения (УЗО) с номинальным отключающим дифференциальным током не более 30 мА.

2

Какие виды проверок знаний установлены для электротехнического персонала?

Проверка знаний работников подразделяется на первичную и периодическую (очередную и внеочередную).

3

Что необходимо выполнить работнику перед началом работы с ручными электрическими машинами?

Перед началом работ с ручными электрическими машинами, переносными электроинструментом следует:

- определить по паспорту класс машины или инструмента;

- проверить комплектность и надежность крепления деталей;

- убедиться внешним осмотром в исправности кабеля (шнура), его защитной трубки и штепсельной вилки, целости изоляционных деталей корпуса, рукояток и крышек щеткодержателей;

- проверить четкость работы выключателя;

- выполнить (при необходимости) тестирование устройства защитного отключения (УЗО);

- проверить работу электроинструмента или машины на холостом ходу;

- проверить у машины I класса исправность цепи заземления (корпус машины – заземляющий контакт вилки).

4

Какие плакаты и знаки безопасности относятся к указательным?

Плакат указательный «ЗАЗЕМЛЕНО».

5

Какую жидкость (раствор) можно вливать в рану при ранении конечности?

Запрещается промывать рану водой и вливать в рану спиртовые или любые другие растворы.

6

В каких случаях проводится дозарядка или перезарядка баллонов и емкостей установок пожаротушения?

Баллоны и емкости установок пожаротушения, масса огнетушащего вещества и давление в которых ниже расчетных значений на 10% и более, подлежат дозарядке или перезарядке.

БИЛЕТ № 25

1

Что понимается под напряжением шага?

Напряжение между двумя точками на поверхности земли, на расстоянии 1 м одна от другой, которое принимается равным длине шага человека.

2

Какие надписи должны быть нанесены на штепсельных розетках в помещениях с использованием напряжения двух и более номиналов?

В помещениях, в которых используется напряжение двух или более номиналов, на всех штепсельных розетках должны быть надписи с указанием номинального напряжения.

3

На какие группы подразделяется электротехнический персонал, обслуживающий электроустановки?

Персонал административно-технический

Руководители и специалисты, на которых возложены обязанности по организации технического и оперативного обслуживания, проведения ремонтных, монтажных и наладочных работ в электроустановках

Персонал оперативный

Персонал, осуществляющий оперативное управление и обслуживание электроустановок (осмотр, оперативные переключения, подготовку рабочего места, допуск и надзор за работающими, выполнение работ в порядке текущей эксплуатации).

Персонал оперативно-ремонтный

Ремонтный персонал, специально обученный и подготовленный для оперативного обслуживания в утвержденном объеме закрепленных за ним электроустановок.

Персонал ремонтный

Персонал, обеспечивающий техническое обслуживание и ремонт, монтаж, наладку и испытание электрооборудования.

4

Для каких электроустановок предназначены однополюсные указатели напряжения до 1000 В?

Однополюсные указатели напряжения работающие при протекании емкостного тока предназначены для ЭУ только переменного тока.

5

Какие правила оказания помощи установлены при попадании едких химических веществ в глаза?

Раздвинуть осторожно веки пальцами и подставить под струю холодной воды.

Промыть глаза под струей холодной воды так, чтобы она стекала от носа кнаружи.

6

Что необходимо выполнить при установке на объекте огнетушителей

Каждый огнетушитель, установленный на объекте, должен иметь порядковый номер, нанесенный на корпус белой краской. На него заводят паспорт по установленной форме.