ПРАВИЛА УСТРОЙСТВА ЭЛЕКТРОУСТАНОВОК

№

п/п

Вопрос

Ответ

1

Что называется электроустановкой?

Совокупность машин, аппаратов, линий и вспомогательного оборудования (вместе с сооружениями и помещениями, в которых они установлены), предназначенных для производства, преобразования, трансформации, передачи, распределения электрической энергии и преобразования её в другой вид энергии.

2

Какая классификация помещений в отношении опасности поражения людей электрическим током установлена нормативными документами?

1.Помещения без повышенной опасности, в которых отсутствуют условия, создающие повышенную или особую опасность.

2.Помещения с повышенной опасностью, характеризующиеся наличием в них одного из следующих условий, создающих повышенную опасность: сырости (влажность более 75 %) или токопроводящей пыли; токопроводящих полов,

высокой температуры (выше 35 °С); возможности одновременного прикосновения человека к имеющим соединение с землей металлоконструкциям зданий, технологическим аппаратам, механизмам и т.п., с одной стороны, и к металлическим корпусам электрооборудования - с другой.

3.Особо опасные помещения, характеризующиеся наличием одного из следующих условий, создающих особую опасность:

особой сырости; химически активной или органической среды;

одновременно двух или более условий повышенной опасности.

4.Территории размещения наружных электроустановок. В отношении опасности поражения людей электрическим током эти территории приравниваются к особо опасным помещениям.

3

Какие помещения называются сырыми?

Сырыми помещениями называются помещения, в которых относительная влажность воздуха длительно превышает 75%

4

Какие способы обеспечения безопасности обслуживающего персонала установлены в электроустановках

1. Закрытие и ограждение токоведущих частей.

2. Применение блокировки аппаратов и ограждающих устройств.

3. Применение предупреждающей сигнализации, надписей и плакатов; использование средств защиты и приспособлений.

5

Какие из условий относят помещения к особо опасным помещениям в отношении опасности поражения людей током

Особо опасные помещения, характеризующиеся наличием одного из следующих условий, создающих особую опасность:

особой сырости; химически активной или органической среды;

одновременно двух или более условий повышенной опасности.

6

Какое цветовое обозначение установлено для шины, используемой в качестве нулевойв ЭУ напряжением

до 1000 В с глухозаземленной нейтралью?

Полосами одинаковой ширины желтого и зеленого цветов

7

Какое цветовое обозначение установлено для шин переменного однофазного тока?

Шина, присоединенная к началу обмотки источника питания - желтый цвет; к концу обмотки - красный.

8

Какое цветовое обозначение установлено для шин ЭУ переменного трехфазного тока?

Шины фазы А – желтым, фазы В – зеленым, фазы С – красным

9

Какой цвет установлен для нулевого рабочего проводника электрической сети?

Голубой

10

Какой цвет установлен для совмещенных нулевых защитных и нулевых рабочих (PEN) проводников?

Голубой цвет по всей длине и желто-зеленые полосы на концах.

11

Какое расстояние должно быть между доступными одновременному прикосновению проводящими частями в ЭУ до 1000В, размещенными вне зоны досягаемости?

Не менее 2,5 метров

12

К каким помещениям, в отношении опасности поражения людей электрическим током, относятся помещения с постоянной температурой более +35 градусов С?

К помещениям с повышенной опасностью.

13

Что понимается под косвенным прикосновением?

Электрический контакт людей или животных с открытыми проводящими частями, оказавшимися под напряжением при повреждении изоляции.

14

Что понимается под электрической сетью с глухозаземленной нейтралью?

Сеть, у которой нейтраль трансформатора или генератора присоединена к заземляющему устройству непосредственно или через малое сопротивление.

15

Что понимается под электрической сетью с изолированной нейтралью?

Сеть, у которой нейтраль трансформатора или генератора не присоединена к заземляющему устройству или присоединена к нему через приборы сигнализации, измерения, защиты и подобные им устройства, имеющие большое сопротивление.

16

Что понимается под напряжением прикосновения?

Напряжение между двумя проводящими частями или между проводящей частью и землей при одновременном прикосновении к ним человека или животного.

17

Что понимается под напряжением шага?

Напряжение между двумя точками на поверхности земли, на расстоянии 1 метра одна от другой, которое принимается равным длине шага человека.

18

При каком минимальном значении напряжения переменного и постоянного тока следует выполнять защиту от косвенного прикосновения в помещениях без повышенной опасности?

Во всех случаях, если напряжение в электроустановке превышает 120 В постоянного тока.

19

В каком случае не требуется выполнять защиту от прямого прикосновения в помещениях без повышенной опасности с электроустановками переменного тока и постоянного тока?

Защита от прямого прикосновения не требуется, если электрооборудование находится в зоне системы уравнивания потенциалов, а наибольшее рабочее напряжение не превышает 25 В переменного или 60 В постоянного тока в помещениях без повышенной опасности.

20

Какие открытые проводящие части электрооборудования должны быть присоединены к глухозаземленной нейтрали для защиты при косвенном прикосновении?

1) корпуса электрических машин, трансформаторов, аппаратов, светильников и т. д.; 2) приводы электрических аппаратов; 3) вторичные обмотки измерительных трансформаторов; 4) каркасы распределительных щитов, щитов управления, и прочих щитков и шкафов где установлено электро оборудование; 5) металлические конструкции, на которых устанавливается электрооборудование и кабеля; 6) металлические оболочки и броня контрольных и силовых кабелей и проводов проложенных на общих металлических конструкциях, например в коробах, лотках и т.п. с кабелями и проводами на более высокие напряжения; 7) металлические корпуса передвижных и переносных электроприемников; 8) электрооборудование, размещенное на движущихся частях станков, машин и механизмов.

21

Что должно быть использовано для защиты от поражения электрическим током в нормальном режиме при прямом прикосновении?

По отдельности или в сочетании следующие меры: основная изоляция токоведущих частей; ограждения и оболочки; установка барьеров; размещение вне зоны досягаемости; применение сверхнизкого (малого) напряжения; для дополнительной защиты следует применять УЗО с номинальным дифференциальным током не более 30 мА

22

Что должно быть использовано для защиты от поражения электрическим током в случае повреждения изоляции при косвенном прикосновении?

По отдельности или в сочетании следующие меры: защитное заземление; автоматическое отключение питания; уравнивание потенциалов; выравнивание потенциалов; двойная или усиленная изоляция; сверхнизкое (малое) напряжение; защитное электрическое разделение цепей; изолирующие, (непроводящие) помещения, зоны, площадки.

23

Каким должно быть сопротивление заземляющего устройства для нейтрали трансформатора при линейном напряжении источника трехфазного тока 380 и 220 В?

В любое время года должно быть

не более 4 Ом. при 380В.

не более 8 Ом. при 220В.

24

Какую функцию выполняют устройства защитного отключения (УЗО), применяемые в ЭУ до 1000 В?

Для дополнительной защиты от прямого прикосновения.

25

Что должно быть нанесено на опорах воздушной линии напряжением 0,4 кВ?

На опорах ВЛ на высоте не менее 2 м от земли через 250 м на магистрали ВЛ должны быть установлены (нанесены): порядковый номер опоры; плакаты, на которых указаны расстояния от опоры ВЛ до кабельной линии связи (на опорах, установленных на расстоянии менее 4 м до кабелей связи), ширина охранной зоны и телефон владельца ВЛ

26

Что следует понимать под прямым прикосновением в электроустановках

Электрический контакт людей и животных с открытыми проводящими частями, находящимися под напряжением.

27

Заземление (определение, принцип работы, нормы сопротивления заземления)

Защитное заземление – это преднамеренное электрическое соединение нетоковедущих металлических частей электроустановок с землей, необходимое для защиты людей от поражения электрическим током при прикосновении к металлическим нетоковедущим частям, которые могут оказаться под напряжением в результате повреждения изоляции.

Принцип работы: Понижение напряжения между корпусом и землей до безопасного значения, то есть уменьшение напряжения прикосновения, и следовательно тока, протекающего через организм человека.

Нормы сопротивления заземления:

- На ОУС = 4 Ом

- на ТП = 8 Ом

- R тела человека = 1 КОм

Сечение проводника:

- до 1000 В - не менее 16 кв. мм

- Свыше 1000 В – не менее 25 кв. мм

28

Защитное зануление в электроустановках напряжением до 1 кВ (определение, принцип работы)

ЗАНУЛЕНИЕМ - называется преднамеренное электрическое соединение с нулевым защитным проводником металлических нетоковедущих частей, которые могут оказаться под напряжением.

Принцип работы: Превратить пробой на корпус в однофазное короткое замыкание, вызвать срабатывание защиты и отключение электроустановки от питающей сети в минимально короткий срок.

ПРАВИЛА ТЕХНИЧЕСКОЙ ЭКСПЛУАТАЦИИ ЭЛЕКТРОУСТАНОВОК ПОТРЕБИТЕЛЕЙ

1

За что несут персональную ответственность работники, непосредственно обслуживающие электроустановки?

за нарушения, происшедшие по их вине, а также за неправильную ликвидацию ими нарушений в работе электроустановок на обслуживаемом участке;

2

За что несут персональную ответственность работники, проводящие ремонт оборудования?

за нарушения в работе, вызванные низким качеством ремонта;

3

Кому и когда должен сообщить работник, заметивший неисправности электроустановки или средств защиты?

Работник должен немедленно сообщить об этом своему непосредственному руководителю, а в его отсутствие – вышестоящему руководителю.

4

В каком случае электротехнический персонал обязан пройти стажировку (производственное обучение)?

При назначения на самостоятельную работу или при переходе на другую работу (должность), связанную с эксплуатацией электроустановок, а также при перерыве в работе в качестве электротехнического персонала свыше 1 года.

5

На какой состав подразделяется электротехнический персонал?

подразделяется на:

- административно-технический;

- оперативный;

- ремонтный;

- оперативно-ремонтный.

6

С каким персоналом обязательной формой работы (профессиональной подготовки) является дублирование?

С оперативным и оперативно-ремонтным персоналом.

7

Какая продолжительность дублирования установлена для оперативного персонала?

От 2-х до 12 смен.

8

Каким требованиям должны удовлетворять работники, принимаемые для выполнения работ в электроустановках?

должны иметь профессиональную подготовку, соответствующую характеру работы.

9

Какие виды проверок знаний установлены для электротехнического персонала?

Первичная - у работников, впервые поступивших на работу, или при перерыве в проверке знаний более 3 лет; очередная; внеочередная - при нарушении правил.

10

В каком случае проводится внеочередная проверка знаний?

Внеочередная проверка знаний проводится независимо от срока проведения предыдущей проверки:

- при введении в действие у Потребителя новых или переработанных Норм и Правил;

- при установке нового оборудования, реконструкции или изменении главных электрических и технологических схем (необходимость внеочередной проверки в этом случае определяет технический руководитель);

- при назначении или переводе на другую работу, если новые обязанности требуют дополнительных знаний Норм и Правил;

- при нарушении работниками требований нормативных актов по охране труда;

- по требованию органов государственного надзора;

- по заключению комиссий, расследовавших несчастные случаи с людьми или нарушения в работе энергетического объекта;

- при повышении знаний на более высокую группу;

- при проверке знаний после получения неудовлетворительной оценки;

- при перерыве в работе в данной должности > 6 мес.

11

В каком случае проводится очередная проверка знаний?

1 раз в год, если работник не меняет должности

12

Продлевается или нет срок действия удостоверения для работников, получивших неудовлетворительную оценку при проверке знаний?

Продлевается автоматически до срока, назначенного комиссией для второй проверки, если нет записанного в журнал проверки знаний специального решения комиссии о временном отстранении работника от работы в электроустановках.

13

Какой вид проверки установлен для работника, повышающего знания на более высокую группу?

Внеочередная

14

Какие надписи должны быть нанесены на штепсельных розетках в помещениях с использованием напряжения двух и более номиналов?

Надписи с указанием номинального напряжения.

15

Какие условия должны быть выполнены перед проведением земляных работ вблизи кабельных трасс?

Исполнитель должен обеспечить надзор за сохранностью кабелей на весь период работ, а вскрытые кабели укрепить для предотвращения их провисания и защиты от механических повреждений. На месте работы должны быть установлены сигнальные огни и предупреждающие плакаты.

16

Какое напряжение для питания переносных электрических светильников должно применяться в помещениях с повышенной опасностью?

Для питания переносных (ручных) электрических светильников в помещениях с повышенной опасностью и в особо опасных помещениях должно применяться напряжение не выше 50 В.

17

Какое напряжение для питания переносных электрических светильников должно применяться в наружных установках?

При работах в особо неблагоприятных условиях и в наружных установках - не выше 12 В.

МЕЖОТРАСЛЕВЫЕ ПРАВИЛА ПО ОХРАНЕ ТРУДА

1

Какие работы в электроустановках считаются верхолазными?

Работы, выполняемые на высоте более 5 м от поверхности земли, перекрытия или рабочего настила, над которым производятся работы непосредственно с конструкций или оборудования при их монтаже или ремонте, при этом основным средством, предохраняющим работающих от падения, является предохранительный пояс.

2

Для каких целей применяется защитное заземление?

Защитное заземление - заземление частей электроустановки с целью обеспечения электробезопасности.

3

Какой персонал может выполнять работы в электроустановках в порядке текущей эксплуатации согласно перечню?

Оперативный

4

Кому должен сообщать работник о замеченных им нарушениях, представляющих опасность для людей?

Вышестоящему руководителю

5

При каких условиях считается, что работы в электроустановках выполняются на высоте?

Работник находится на расстоянии менее 2-х метров от не огражденного перепада по высоте 1,3 м и более.

6

Какая электроустановка относится к действующей?

Электроустановка или ее часть находится под напряжением, либо на которую напряжение может быть подано.

7

Кто имеет право единоличного осмотра электроустановок и электрической части технологического оборудования напряжением до 1000 В?

Работник из оперативного персонала с группой 3, или из административного персонала с группой 4 по письменному распоряжению руководителя организации.

8

Разрешается ли при единоличном осмотре электроустановок открывать двери щитов и сборок?

Разрешается

9

Разрешается ли выполнение какой-либо работы во время осмотра электроустановок?

Не разрешается

10

На какое расстояние разрешается приближаться к месту замыкания провода воздушной линии электропередачи на землю без средств защиты?

8 метров и более.

11

Допускается ли снимать и устанавливать предохранители в электрических сетях под напряжением и нагрузкой?

Снимать и устанавливать предохранители следует при снятом напряжении. Допускается снимать и устанавливать предохранители, находящиеся под

напряжением, но без нагрузки. Под напряжением и под нагрузкой допускается заменять: предохранители во вторичных цепях, предохранители трансформаторов напряжения и предохранители пробочного типа.

12

По какому документу можно выполнять работы в действующих электроустановках?

Наряд-допуск, распоряжение, перечень работ в порядке текущей эксплуатации

13

Какая последовательность организационных мероприятий установлена для обеспечения безопасности работ в электроустановках?

Оформление работ( наряд, распоряжение, перечень в порядке текущей эксплуатации), допуск к работе, надзор во время работы, оформление перерывов, перевод на другое рабочее место, окончание работы

14

Кому предоставлено право выдачи распоряжений для проведения работ в электроустановках напряжением до 1000 В?

Работнику из административно-технического персонала с группой 4.

15

Для каких целей назначается наблюдающий при проведении работ в электроустановках?

Для надзора за бригадой, не имеющей право самостоятельно работать в электроустановках.

16

На какой максимальный срок (календарные дни) разрешается выдавать наряд на работы в электроустановках?

Не более 15 дней.

17

Какой срок хранения установлен для нарядов, работы по которым полностью закончены и если при выполнении этих работ не имели место аварии, инциденты или несчастные случаи?

30 суток.

18

Где следует хранить наряды, по которым работы полностью закончены, но имел место несчастный случай?

В архиве организации.

19

Какой срок действия установлен для распоряжений на выполнение работ в электроустановках?

Распоряжение имеет разовый характер, срок его действия определяется продолжительностью рабочего дня исполнителей. При необходимости продолжения работы, при изменении условий работы или состава бригады распоряжение должно отдаваться заново. При перерывах в работе в течение дня повторный допуск осуществляется производителем работ.

20

Какая последовательность выполнения технических мероприятий установлена для обеспечения безопасности работ со снятием напряжения?

Произведены необходимые отключения и приняты меры, препятствующие подаче напряжения на раб. месте; вывешены запрещающие плакаты; проверено отсутствие напряжения; наложено заземление; вывешены указательные, предупреждающие и предписывающие плакаты.

21

Где вывешиваются запрещающие плакаты при выполнении технических мероприятий, обеспечивающих безопасность работ со снятием напряжения на присоединениях напряжением до 1000 В., не имеющих коммутационных аппаратов?

Плакат «Не включать! Работают люди» должен быть вывешен у снятых предохранителей КРУ (комплектные распределительные устройства).

22

Где вывешивается плакат ЗАЗЕМЛЕНО при выполнении технических мероприятий, обеспечивающих безопасность работ в электроустановках со снятием напряжения?

Плакаты «Заземлено» должен быть вывешен на приводах

разъединителей, отделителей и выключателей нагрузки, при ошибочном включении которых может быть подано напряжение на заземленный участок электроустановки. Так же на ключах и кнопках дистанционного управления коммутационными аппаратами.

23

Кому разрешено устанавливать и снимать переносные заземления в электроустановках напряжением до 1000 В?

Одному работнику из оперативного персонала с группой 3.

24

Что необходимо предварительно выполнить перед работой в кабельных подземных сооружениях?

Обеспечить естественную или принудительную вентиляцию (содержание кислорода не менее 20%), проверку отсутствия газов.

25

Кто может выполнять работы в подземных кабельных сооружениях?

Три работника, из которых два страхующих, производитель с 4 группой, по наряду.

26

Какие требования предъявляются к работникам, выполняющим измерения сопротивления изоляции мегаомметром?

Должны иметь 3 группу

27

Кто может осуществлять подключение вспомогательного оборудования для ручных электрических машин к электрической сети

Электротехнический персонал с группой 3, эксплуатирующий эту электрическую сеть.

28

Что необходимо выполнить работнику перед началом работы с ручными электрическими машинами?

Определить по паспорту класс машины или инструмента, проверить комплектность и крепление деталей, провести внешний осмотр, проверить четкость работы выключателя, выполнить тестирование УЗО, проверить работу на холостом ходу, проверить у машин 1 класса цепь заземления.

29

На какое напряжение должны подключаться переносные электрические светильники в особо опасных помещениях?

Не выше 50 В.

30

На какое напряжение должны подключаться переносные светильники при работе в особо неблагоприятных условиях (металлические резервуары)?

Не выше 12 В.

31

Разрешается или не допускается работа с ручными электрическими машинами с приставных лестниц?

Не допускается

32

Какие документы должны иметь командированные работники по прибытии в организацию для проведения работ в электроустановках?

Сопроводительное письмо и удостоверение о проверке знаний, норм и правил работы в электроустановках

33

Какие из мероприятий необходимо провести с командированным персоналом в организации, где этот персонал будет работать в электроустановках?

Вводный и первичный инструктаж

34

В каком случае командированному персоналу предоставляется право работы в действующих электроустановках в качестве производителей работ и членов бригады?

После оформления, разрешения руководителя организации-заказчика резолюцией на сопроводительном письме или письменном указании.

35

Кто имеет право проводить инструктаж командированного персонала перед проведением им работ в электроустановках организации - владельца напряжением до 1000 В.?

Работник из административно-технического персонала с группой 5 или оперативного персонала с группой 4.

36

Кто проводит подготовку рабочего места и допуск командированного персонала к работам в электроустановках организации - владельца?

Работники организации, в электроустановке которой проводятся работы.

37

Кто проверяет подготовку рабочего места перед допуском бригады к работе?

Ответственный руководитель, производитель и допускающий

38

Кто может осуществлять повторный допуск по наряду в последующие дни на подготовленное рабочее место?

Допускающий или с его разрешения ответственный руководитель (производитель работ, если есть разрешение в строке «Отдельные указания»)

39

Какой определен порядок установки переносных заземлений?

Сначала к заземляющему устройству, затем после проверки отсутствия напряжения к оборудованию.

40

Какие условия должны быть выполнены для включения электроустановки после полного окончания работы?

Убедиться в готовности к включению, снять временные ограждения, плакаты, заземления, восстановить постоянное ограждение.

ИНСТРУКЦИЯ ПО ПРИМЕНЕНИЮ И ИСПЫТАНИЮ СРЕДСТВ ЗАЩИТЫ, ИСПОЛЬЗУЕМЫХ В ЭЛЕКТРОУСТАНОВКАХ

1

Для каких электроустановок предназначены однополюсные указатели напряжения до 1000 В.?

Для электроустановок переменного тока

2

К какому виду средств защиты относятся запрещающие плакаты безопасности?

К электрозащитным средствам и к средствам защиты от электрических полей повышенной напряженности

3

К какому виду средств защиты относятся пояса предохранительные?

Относятся к средствам индивидуальной защиты и от падения с высоты.

4

Какие требования предъявляются к страховочному канату?

Стальные должны соответствовать ГОСТу ; хлопчатобумажный - диаметром не менее 15 мм, длиной 10м. Разрывная статическая нагрузка не менее 7000 Н.

5

Какие изолирующие электрозащитные средства в электроустановках напряжением до 1000 В. относятся к основным?

- изолирующие штанги, клещи;

- указатели напряжения;

- диэлектрические перчатки;

- слесарно-монтажный инструмент с изолирующими рукоятками.

6

Какие изолирующие электрозащитные средства в электроустановках напряжением до 1000В. относятся к дополнительным?

- диэлектрические галоши;

- диэлектрические ковры;

- переносные заземления;

- изолирующие подставки и накладки;

- оградительные устройства;

- плакаты и знаки безопасности.

7

Что обязан выполнять персонал организации перед каждым применением средств защиты?

Проверить: его исправность, отсутствие внешних повреждений и загрязнений, по штампу срок годности.

8

В каком случае можно использовать контрольные лампы для проверки отсутствия напряжения в электроустановках напряжением 0,4 кВ?

Не допускается

9

Какое значение напряжения индикации должно быть для указателей напряжения до 1000 В.?

Не более 50 В

10

Обязательно ли применение диэлектрических перчаток при пользовании однополюсными указателями напряжения до 1000В.

Применение не допускается

11

Каким образом следует проверять перчатки диэлектрические на отсутствие прокола?

Путем скручивания в сторону пальцев

12

Какая периодичность испытаний установлена для ковров резиновых диэлектрических?

В эксплуатации ковры и подставки не испытывают. Их отбраковывают при осмотрах. Ковры следует очищать от загрязнений и осматривать не реже 1 раза в 6 мес.

13

Какое минимальное сечение (кв.мм) проводов переносных заземлений установлено в электроустановках напряжением до 1000 В.?

Не менее 16 мм кв.

14

На какие виды подразделяются плакаты и знаки безопасности?

Запрещающие, предупреждающие, предписывающие, указательные.

15

Какая периодичность испытаний установлена для диэлектрических резиновых перчаток?

Один раз в 6 мес.

16

Какие плакаты и знаки безопасности относятся к указательным?

"ЗАЗЕМЛЕНО".

17

Какие плакаты и знаки безопасности относятся к запрещающим?

Не включать! Работают люди.

18

Какая длина установлена для диэлектрических перчаток?

Не менее 350 мм.

МЕЖОТРАСЛЕВАЯ ИНСТРУКЦИЯ ПО ОКАЗАНИЮ ПЕРВОЙ ПОМОЩИ ПРИ НЕСЧАСТНЫХ СЛУЧАЯХ НА ПРОИЗВОДСТВЕ

1

Какая последовательность действий принята для оказания первой помощи на месте происшествия?

Начать с восстановления сердечной деятельности и дыхания, приступить к временной остановке кровотечения. Нет сознания и пульса→реанимация;

Нет сознания, есть пульс→повернуть на живот и очистить ротовую полость;

Артериальное кровотечение→наложить жгут;

Наличие ран→наложить повязки;

Признаки перелома костей →наложить шины.

2

Какие действия выполняются при проведении искусственного дыхания?

Зажать нос, захватить подбородок, запрокинуть голову пострадавшего и сделать максимальный выдох ему в рот желательно через салфетку.

3

В течение какого времени необходимо проводить реанимацию пострадавшему при внезапной смерти?

либо до появления самостоятельного дыхания и самостоятельной сердечной деятельности либо до прибытия медицинских работников либо до появления биологической смерти.

4

Какие установлены правила реанимации, независимо от количества участников оказывающих помощь.

Один – 2 вдоха, 30 надавливаний

Двое – 2 вдоха, 5 надавливаний

5

Какие действия необходимо предпринять для оказания помощи пострадавшему, который находится в состоянии комы (нет сознания, но есть пульс)?

Повернуть на живот, удалить слизь и содержимое желудка, приложить холод к голове.

6

В каком месте необходимо прижимать артерию в случае артериального кровотечения?

На конечностях - выше места кровотечения, на шее и голове - ниже раны или в ране.

7

На какое время накладывается жгут при артериальном кровотечении?

Не более чем на 1 час.

8

Какую жидкость (раствор) можно вливать в рану при ранении конечности?

Не допускается.

9

Как обрабатывать ожоги на месте происшествий?

Без нарушения целостности ожоговых пузырей: подставить под струю воды на 10 - 15 минут, и (или) приложить холод на 20 - 30 минут. При нарушении целостности: накрыть рану сухой чистой тканью и поверх ткани приложить холод.

10

Какие правила оказания помощи установлены при попадании едких химических веществ в глаза?

Раздвинуть осторожно веки пальцами и подставить под струю холодной воды, промыть глаза водой, чтобы она стекала от носа кнаружи. Нельзя применять нейтрализующую жидкость.

11

Что необходимо выполнить в случае перелома конечности?

Зафиксировать с помощью шин или подручных средств, при открытых переломах сначала наложить повязку.

12

Какие установлены правила перемещения человека в зоне шагового напряжения?

Передвигаться следует в резиновых ботах или галошах либо "гусиным шагом" - пятка шагающей ноги, не отрываясь от земли, приставляется к носку другой ноги.

13

Какой порядок действий оказания первой помощи пострадавшему установлен в случае обморока?

Убедиться в наличии пульса на сонной артерии, освободить грудную клетку от одежды и расстегнуть поясной ремень, приподнять ноги, надавить на болевую точку, вызвать врача.

14

Какой установлен порядок действий в случае отравления пострадавшего ядовитыми газами?

Вынести на свежий воздух, в случае отсутствия сознания и пульса на солнечной артерии - приступить к комплексу реанимации, в случае потери сознания более 4 минут - повернуть на живот и приложить холод к голове, вызвать "Скорую помощь".

15

При каких показаниях следует немедленно наложить кровоостанавливающий жгут?

- алая кровь бьет фонтанирующей струей;

- над раной образуется валик из вытекающей крови;

- лужа крови возле пострадавшего или большое кровавое пятно на одежде.

16

Какие признаки свидетельствуют о внезапной (клинической) смерти пострадавшего?

- нет сознания;

- нет реакции зрачков на свет;

- нет пульса на сонной артерии.

17

Какие признаки свидетельствуют о биологической смерти пострадавшего?

1.Высыхание роговицы глаза (появление селедочного блеска);

2.Деформация зрачка при осторожном сжатии глазного яблока пальцами;

3.Появление трупных пятен.

18

По каким признакам можно определить, что человек находится в состоянии комы?

- нет сознания более 4 минут;

- есть пульс на сонной артерии.

19

Какие признаки определяют наличие у пострадавшего артериального кровотечения?

1.Алая кровь из раны бьет фонтанирующей струей;

2.Над раной образуется валик из вытекающей крови;

3.Большое кровавое пятно на одежде или лужа крови возле пострадавшего.

20

Какие признаки определяют наличие у пострадавшего венозного кровотечения?

1.Кровь пассивно стекает из раны;

2.Очень темный цвет крови.

21

Какие признаки определяют наличие обморока у человека?

1. кратковременная потеря сознания (не более 3-4 минут); 2. потере сознания предшествует резкая слабость, головокружение, звон в ушах; 3.потемнение в глазах.

22

При каких показаниях следует переносить пострадавшего только на животе?

1.В состоянии комы;

2.При частой рвоте;

3.В случае ожогов спины и ягодиц;

4.При подозрении на повреждение спинного мозга, когда в наличии имеются только брезентовые носилки.

23

При каких показаниях следует переносить и перевозить пострадавшего только сидя или полусидя?

- при проникающих ранениях грудной клетки;

- при ранении шеи.

24

При каких показаниях можно переносить пострадавшего только на спине с приподнятыми или согнутыми в коленях ногами?

- при проникающих ранениях брюшной полости;

- при большой кровопотери и при подозрении на внутреннее кровотечение.

25

Первая помощь при ушибах, растяжении связок.

При ушибах - на ушиб накладывают давящую повязку, а сверху лед. Если есть ссадина, то ее еще смазывают йодом.

При растяжении связок – делается тугая повязка чтоб фиксировать связки, холод.

ПРАВИЛА ПОЖАРНОЙ БЕЗОПАСНОСТИ

1

Что должно быть выполнено на каждом объекте (организации) для обеспечения пожарной безопасности?

Разработаны инструкции о мерах пожарной безопасности для каждого пожароопасного и взрывоопасного помещения.

2

В каком случае работники предприятия должны допускаться к работе в соответствии с правилами пожарной безопасности?

Все работники организаций должны допускаться к работе только после прохождения противопожарного инструктажа.

3

Какие электроустановки и электроприборы могут не выключаться по окончании рабочего дня в помещениях без дежурного персонала для обеспечения пожарной безопасности?

Дежурное освещение, установки пожаротушения и противопожарного водоснабжения, пожарная и охранно-пожарная сигнализация.

4

В каких случаях проводится дозарядка или перезарядка баллонов и емкостей установок пожаротушения?

Давление в которых ниже расчетных значений на 10 % и более.

5

Какие должны быть действия сотрудника организации, обнаружившего пожар или признаки горения?

Сообщить по телефону в пожарную охрану, принять меры по эвакуации людей, по возможности приступить к тушению пожара, сохранению материальных ценностей.

6

К какому классу относятся пожары, связанные с горением электроустановок?

Класс Е

7

Есть ли необходимость устанавливать огнетушители в помещениях, оборудованных автоматическими стационарными установками пожаротушения?

Помещения, оборудованные автоматическими стационарными установками пожаротушения, обеспечиваются огнетушителями на 50%, исходя из их расчетного количества.

8

Что необходимо выполнить при установке на объекте огнетушителей?

Каждый огнетушитель должен иметь порядковый номер, нанесенный на корпус масляной краской, и заводской паспорт, установленной формы.

9

Где должны размещаться первичные средства пожаротушения?

На видных местах вблизи от выходов из помещений на высоте не более 1,5 м.

10

Огнетушители, их типы, правила применения и пользования.

Огнетушители делятся на переносные (массой до 20 кг) и передвижные (массой не менее 20, но не более 400 кг). По виду применяемого огнетушащего вещества огнетушители подразделяют на: водные, пенные, порошковые, газовые, комбинированные.

Пенные огнетушители применяют для тушения пеной начинающихся загораний почти всех твердых веществ, а также горючих и легковоспламеняющихся жидкостей на площади не более 1м²

Углекислотные огнетушители Предназначены для тушения загораний на электрифицированном транспорте, а так же электроустановок под напряжением до 380 В.

Порошковые огнетушители

Используют для тушения небольших очагов загораний горючих жидкостей, газов, электроустановок напряжением до 1000В.

11

Пожарная безопасность в производственных помещениях.

Противопожарная безопасность включает в себя комплекс организационных и технических мероприятий.

1) В помещении должна быть инструкция о мерах пожарной безопасности. 2) Необходимо соблюдать чистоту и порядок в помещении.

3) Курить только в специально отведенных местах. 4) Не загромождать проходы в помещении. 5) Осматривать помещение после работы.

Запрещается:

1) Уборка помещений химическими веществами. 2) Применять не калиброванные вставки и жучки. 3) Пользоваться приборами с открытыми спиралями нагрева. 4) Оставлять включенными электроприборы. 5) Хранить легко воспламеняющиеся вещества.

Во всех технических помещениях станций радиотрансляционных узлов следует иметь углекислотные огнетушители, а при использовании в мощном усилительном оборудовании масляных трансформаторов, кроме того, ящик с песком и лопатой.

12

Порядок хранения и правила применения пожароопасных веществ и материалов.

В помещения ОУС хранение огнеопасных и легковоспламеняющихся жидкостей и горюче-смазочных материалов - запрещено.

Обтирочные материалы должны храниться в закрытых металлических ящиках емкостью не более 0.5 кубических метра. Пожароопасные вещества должны храниться на складе в специально отведённых местах. Горючие жидкости в железных бочках. В помещениях, где хранятся горюче-смазочные материалы пользование керосиновыми лампами, открытым огнем и курение запрещено. Случайно пролитые топливо или масла должны быть немедленно засыпаны песком. В случае воспламенения жидкого топлива или изоляции на токоведущих частях электростанции необходимо пользоваться углекислотным огнетушителем.